Emergency Measures for Safety Failure of Boiler Post 1. When the water level glass tube bursts or false water level occurs, the cock leaks. Temporarily stop boiler operation, close water pipe valve, replace glass pipe or cock, add or replace filler, tighten pressure cap.Flush the connecting pipe and strengthen the drainage. 2. Pressure gauge failure. Stop boiler operation, close meter control valve, replace pressure gauge or cock.Clean or blow the pressure gauge passage and adjust the pointer to the correct position. 3. Safety valve failure, steam leakage, over- pressure opening or opening under rated pressure, and after exhaust valve spool does not return to the seat, etc. Stop boiler operation and close safety valve.Blow wash or replace the safety valve verified by the quality inspection department of the city. 4. Boiler explosion caused by overheating, corrosion and cracks. overpressure, When an accident occurs, the boiler operation shall be stopped immediately and the power supply of the operating equipment such as the blower and the induced draft fan shall be cut off.Make every effort to reduce the loss of boiler equipment and avoid injuries to personnel.
Emergency Measures for Safety Failure of Boiler Post
Tips: If the document is garbled or fails to read, please download the document
Uploaded by admin on 2019-10-15 15:32:00